- Shangchai generator set
- Cummins generator set
- Yuchai generator set
- Weifang Diesel Generator
- Gasoline generator
- Single-cylinder diesel engine
Contact Songge Mechanical
Cummins generator set-Yuchai generator set-Silent diesel generator-Guangzhou Songge Mechanical and Electrical Co., Ltd.
020-84851836 Consulting Hotline: 020-84851836
曹先生 Contact: Mr. Cao
13609022338 Mobile: 13609022338
020-34865288 Fax: 020-34865288
firstname.lastname@example.org Email: email@example.com
广东省广州市沙湾镇大涌口第二工业区1号 Address: No. 1 Second Industrial Zone, Dayongkou, Shawan Town, Guangzhou City, Guangdong Province
Knowledge of generator fuel
For different models Generator set, most of them Generator manufacturers are equipped with corresponding standard fuel tanks and fuel supply systems for users to purchase. At the same time, it can also be designed as a bottom tank according to user requirements. Can also be designed according to user requirements into a variety of discrete fuel tanks. Users can also design the fuel tank by themselves, but no matter what kind of fuel tank, the installation design must follow the following principles:
1) The storage location of the fuel tank must be safe to prevent fire. The fuel tank or oil drum should be placed in a visible place separately and properly separated. The generator set is far away, and smoking is strictly prohibited.
2) The fuel capacity of the fuel tank should ensure daily supply.
3) After the fuel tank is placed, the highest oil level cannot be 2.5 meters higher than the base of the unit. If the oil level of a large oil depot is higher than 2.5 meters, a daily fuel tank should be added between the large oil depot and the unit to make the pressure of direct oil supply not greater 2.5 meters. Even when the diesel engine is shut down, fuel is not allowed to flow into the diesel engine through the inlet or injection lines by means of gravity
4) The resistance at the oil port must not exceed the specified value when using a clean filter element as specified on the performance data sheet of the diesel engine used. This resistance value is based on half the fuel in the fuel tank.
5) The fuel return resistance must not exceed the requirements on the performance data sheet of the diesel engine used.
6) The connection of the fuel return line should not cause shock waves in the fuel line.